Wago 750-627 WAGO I/O-SYSTEM 750 Supply and segment modules
Bus Extension End Module, Max. no. of Coupler Modules: up to 10 Distance max: 5m (10m see manual), (End Module-Coupler or Coupler-Coupler), Transmission medium: shielded copper wire (ETHERNET-patch cable) 4x2x0,25mm2, twisted pair/double shielding/SPT (Shielded Twisted-Pair), Connection technology: communication/fieldbus: 1x RJ-45
The end module for the internal data bus extension 750-627 is attached to the end of the I/O terminal block like the standard end module 750-600. The block is terminated with the module, to which a connecting cable can be attached with an RJ-45 connector.
Power to the internal electronics is supplied via the internal bus. Together with at least one coupler module for the internal data bus extension 750-628 the module forms a functional unit. The fieldbus coupler/controller carries out all diagnosis and commissioning tasks.
Installation note Attention:
To ensure safe, reliable operating states when using the internal data bus extension 750-627/-628 these states must be registered prior to startup with the following couplers or PLCs (refer to manual for supported couplers/PLCs). You must use the "WAGO Extension Setting" software for this (download: www.wago.com).
Please complete the manufacturing number matrix on the right-hand side of the couplers when updating the firmware and internal operating parameters.
shielded copper wire (ETHERNET patch cable) 4x 2x 0.25 mm², twisted pair, double shielding