Wago 750-627 WAGO-I/O-SYSTEM 750 System Modules
Bus Extension End Module in conjunction with th module 750-628 (coupler module for bus extension), Buscoupler connection: 1x RJ-45 socket, no. of coupler modules: up to 10
The end module for the internal data bus extension 750-627 is attached to the end of the I/O terminal block like the standard end module 750-600. The block is terminated with the module, to which a connecting cable can be attached with an RJ-45 connector.
Power to the internal electronics is supplied via the internal bus. Together with at least one coupler module for the internal data bus extension 750-628 the module forms a functional unit. The fieldbus coupler/controller carries out all diagnosis and commissioning tasks.
Installation note Attention:
To ensure safe, reliable operating states when using the internal data bus extension 750-627/-628 these states must be registered prior to startup with the following couplers or PLCs (refer to manual for supported couplers/PLCs). You must use the "WAGO Extension Setting" software for this (download: www.wago.com).
Please complete the manufacturing number matrix on the right-hand side of the couplers when updating the firmware and internal operating parameters.
shielded copper wire (ETHERNET patch cable) 4x 2x 0.25 mm², twisted pair, double shielding
Wago Fieldbus Coupler PROFINET IO, 3. Generation, Advanced, Baud rate: 100Mbit/s, Coupler conn.: 2x RJ-45, input process image max.: 512 Byte, output process image max.: 512 Byte
Wago 8-channel Digital Output, DC 24V, 0,5A, high-side switching, with Power jumper contacts, short-circuit-proof